正确安装压缩机才能保证压缩机按设计参数工作， 如安装不正确， 将导致压缩机排气温度高、振动大、声音异常等一系列问题。首先将空压机安装在牢固的地面上， 设备基础采用C20混凝土现浇。在空压机厂房每个空压机进气栅所对的墙壁上标高为016m处分别安装两个轴流风机， 进气栅的空气流速不超过015m / s, 且设计进气轴流风机的通风量与压缩机风扇的风量相吻合， 保证了通风系统的通畅。为确保冷却风道中空气的压降不超过30Pa, 设计时要保证从压缩机出口排风管道截面积是空压机顶部截面积的2～3倍。且此通风管道没有缩颈。对其它机型螺杆压缩机， 如冷却风道中空气的压降超橡胶托辊 槽型托辊 皮带托辊 平行托辊 保定搬家 保定搬家电话 保定搬家公型槽模具 一次性止血带 保定水处理设备 一次性止血带 保定空压机 北京真空泵司 保定搬家 铜鼎 铜狮子 过30Pa, 应在冷却风道的出口安装通风风扇， 才能保证压缩机出口温度控制在正常范围内。空压机的通风系统在投运初期出现排气温度高达108℃的现象， 经查找原因分析， 是因为在五月份空气中的树毛比较多， 堵塞了板翅式换热器， 影响了出口气的换热效果。为防止树毛堵塞板翅式换热器， 在两个轴流风机的入口分别加装60目的不锈钢网， 效果十分明显。另外，在以后的运行过程中， 做到定期吹扫板翅式换热器， 以后再没有出现排气温度高的现象。
The correct installation of the compressor can ensure that it operates according to the design parameters. If not installed correctly, it will lead to a series of problems such as high exhaust temperature, high vibration, and abnormal sound of the compressor. Firstly, install the air compressor on a solid ground, and the equipment foundation is cast-in-place with C20 concrete. Two axial flow fans are installed at an elevation of 016m on the wall opposite each air compressor intake grille in the air compressor plant. The air flow rate of the intake grille does not exceed 015m/s, and the designed ventilation volume of the intake axial flow fan matches the air volume of the compressor fan, ensuring the smoothness of the ventilation system. To ensure that the pressure drop of the air in the cooling air duct does not exceed 30Pa, the design should ensure that the cross-sectional area of the exhaust duct from the compressor outlet is 2-3 times that of the top cross-sectional area of the air compressor. And this ventilation duct has no necking. For other types of screw compressors, such as the air pressure drop in the cooling air duct exceeding that of rubber rollers, grooved rollers, belt rollers, parallel rollers, Baoding movers, Baoding movers, Baoding movers, Baoding movers, Baoding movers, and copper lions, which exceed 30Pa, a ventilation fan should be installed at the outlet of the cooling air duct to ensure that the compressor outlet temperature is controlled within the normal range. The ventilation system of the air compressor experienced a phenomenon of exhaust temperature as high as 108 ℃ in the early stage of operation. After investigation and analysis, it was found that there were many tree hairs in the air in May, which blocked the plate fin heat exchanger and affected the heat exchange effect of the outlet gas. To prevent tree hairs from blocking the plate fin heat exchanger, 60 mesh stainless steel mesh was installed at the inlet of the two axial flow fans, which has a very obvious effect. In addition, in the future operation process, the plate-fin heat exchanger should be regularly purged, and there should be no phenomenon of high exhaust temperature in the future.